Goodman Company Recalls Air Conditioning and Heating Units Due to Burn and Fire Hazards
WASHINGTON, D.C. - The U.S. Consumer Product Safety Commission, in cooperation with the firm named below, today announced a voluntary recall of the following consumer product. Consumers should stop using recalled products immediately unless otherwise instructed. It is illegal to resell or attempt to resell a recalled consumer product.
Name of product: Amana, Century, Comfort-Aire, Goodman and York International Packaged Terminal Air Conditioner/Heat Pump ("PTAC") units
Hazard: The power cords on the air conditioning and heating units can overheat, posing burn and fire hazards.
Consumer Contact: For Amana, Goodman and York International-branded units call (800) 366-0339 from 8 a.m. to 5 p.m. CT Monday through Friday. For Comfort-Aire and Century-branded units call toll-free at (877) 442-4482 from 8 a.m. to 5 p.m. ET Monday through Friday. For all products, go to www.amana-ptac.com and click on Recall Info at the bottom right corner of the page for more information.
Units: About 233,500
Description: The recall involves Amana, Century, Comfort-Aire, Goodman and York International-branded Packaged Terminal Air Conditioners and Heat Pumps. The units are rated 230/208 volt, 3.5 kW and are most often installed in walls of hotels, motels, apartment buildings and commercial spaces to provide room climate control. The recalled units are beige with serial numbers ranging from 0701009633 through 0804272329. The brand name is located on the unit's front cover. The serial number is located on the control board plate found by lifting the unit's front cover.
Incidents/Injuries: Goodman has received four reports of power cords smoking or catching on fire. No injuries have been reported.
Remedy: Consumers should immediately stop using and unplug the air conditioning and heating units and call the appropriate number listed above or go to www.amana-ptac.com to request a free replacement power cord. Non-commercial owners will receive free installation of the power cord and inspection of the PTAC control board for damages. If the control board has been damaged by the recalled power cord, non-commercial owners will also receive a free installation of a replacement control board. Commercial owners are being contacted directly and will install the power cord and inspect the control board. If the control board has been damaged by the recalled power cord, Goodman will provide a new control board for commercial owners to install.
Sold through: Goodman and heating and cooling equipment dealers nationwide from January 2007 through June 2008 for between $700 and $1,000.
Importer/Distributor: Goodman Company, L.P. of Houston, Texas
Manufactured in: United States